discount 70% in 2018-10-20 to 2018-10-22
price: USD$ 259.00
freight :USD$7.00,(Postal parcel)
Search Similar or mail to saler or send message to saler
Warm prompt: this shop all product defaults sends neutral (namely does not have LOGO), also may OEM, needs the OEM contact customer service.
In the process of shopping what questions, contact the owner at any time, and look forward to your cooperation!!!
Applicable scopeGas stations, liquefied gas stations, chemical oil, etc.
In the 1 and 2 districts, IIA and IIB T1~T6 explosive atmospheres are used as the illumination of the workshop or the place.
Altitude is not more than 2000m;
The operating environment temperature is -20~+40 centigrade:;
The relative humidity of the surrounding air is not greater than 98% (when the temperature is +25 degrees Celsius);
It is suitable for explosive atmospheres in, T1~T6 and II 1 zones;
Where there is no destruction of metals and insulating properties of gases and vapors;
Where there is no significant shaking and impact vibration;
Pollution class 3;
Installation class II class.
LED explosion proof lamp for LED explosion proof lampTechnical parameter:
Flameproof sign:Exd IIC T6
Rated voltage:AC220V 50Hz
Rated power: 20、30W、40W
Illumination: >100Lx（4.5Meter test
Imaging index: >80
Product execution standards: GB3836.1~2-2010, Q/HH001-2011.
This product is an aluminum alloy shell, after high-speed shot blasting, the surface of high-pressure electrostatic spraying, waterproof, dustproof, anti-corrosion and other functions. Stainless steel exposed fasteners, the transparent parts are made of toughened glass, lamp for flameproof rabbet joint surface structure, but the light source cavity and a wiring cavity, drive cavity, easy installation and maintenance, reliable electrical performance; using high-quality aluminum reflector lamps, improve the use efficiency.
LED lamp installation should check whether the basic technical data on the nameplate is in line with the actual use conditions.
The equivalent diameter of phi 10mm~ Phi 14mm cable line, through the introduction of rubber sealing ring connected to the terminal, with a compression nut will introduce cable tightly, to seal and prevent pulling.
Before use, the wiring should be checked correctly, and whether the fastening screws (bolts) on the shell are tightened. Reliable earthing of cable grounding wire.
Maintenance of "strictly charged cover" and not to knock and damage rubber seal gasket.
In maintenance, if the sealing ring and sealing gasket of the introduced device have aging phenomenon, it should be replaced in time to ensure the protective performance.