discount 70% in 2018-10-18 to 2018-10-20
price: USD$ 693.00
freight :USD$7.00,(Postal parcel)
Search Similar or mail to saler or send message to saler
Price note: CBLD-15W990 yuan / 20W1073 yuan / only
30W1155 yuan / 40W1348 yuan / 50W1430 yuan / only
Freight is subject to actual weight
Applicable to the explosive atmospheres of II A, II B and class C explosive gases;
Apply to combustible dust environment;
Applicable to hazardous places such as petroleum and chemical industry.
When ordering, please specify product type, lamp power, installation method, order quantity and explosion proof sign.
For 200 thousand, with the terminal box ceiling installation, this model is CBLD-20WXH
For special requirements, please specify otherwise.
Explosion proof sign: ExdIICT6/DIPA20A, T6
Operating voltage: 220/36
Thread entry "G": 3/4;
Applicable cable diameter: 9mm- 14mm
Protection level: IP65
Anticorrosive grade: WF1;
Rated power: 20W, 30W, 40W, 50W, 60W;
The lamp is designed and manufactured according to GB3836.1-2000, GB3836.2-2000 and GB12476.1 standards.
The shell of the lamp is made of aluminum alloy, and the surface is electrostatic sprayed.
The main cavity, the outlet cavity adopts flameproof structure, and adopts the dual cavity independent assembly design.
It has the advantages of compact structure, beautiful appearance, waterproof and dustproof, exquisite structure, enlarged heat dissipation space, reduced temperature rise, and improved the service life of light source.
Light source adopts glue sealing structure, good performance, waterproof and dustproof.
Fully exposed fasteners and their accessories are made of stainless steel with high corrosion resistance.
Toughened glass cover has strong impact resistance.
The steel pipe and cable accessories can be used both in and out of the pipeline.
It is easy to install, and a variety of installation methods can be chosen by users.
Installation and explanation
The basic parameters of all technical data and manual inspection on the nameplate shall be in - before installation, line with the actual usage, and check whether the product is damaged, each part is intact, normal.
The power must be cut off before installation and maintenance.
The inlet and outlet cables pass through the rubber sealing ring, the washer and the pressed mother are pressed together to ensure the sealing and the cable can not be loosened, so as to ensure the sealing performance.
The sealing ring will be corroded, cracked, deformed, and the viscosity or hardness change should be replaced in time when the sealing ring changes more than 20% of the factory.
The maintenance disassembly should pay attention to the protection of shell exposure shall not bump scratch free, corrosion, rust proof oil coated 204-01 and regularly.
Must be reliable grounding wire diameter is not less than 4mm2, please don't connect this lamp.
The explosion proof lamp should be checked regularly during use so as to ensure its good operation.
Non professionals are prohibited from opening inspection.
After installation and commissioning, the plugging measures must be done to avoid the volatile moisture entering the shell through the pipeline.